God Freedom Liberty - United States Constitution And Supporters of Our Rights
In Defense of Liberty, Free Speech - by Liberty First by KrisAnne Hall EPISODE DESCRIPTION Are you ready to be offended? Are you able to be offended? This is a challenging show...so be prepared! Liberty says you must be offended from time to time and rejoice in your same right to offend! - http://krisanne-hall.podomatic.com/entry/2016-08-11T16_50_38-07_00 [image: itunes pic]1 year ago
Muslim - Take Over Of America
KINGDOM OF SOROS: INFLUENCE WORLD WITH REFUGEE CRISIS CASH FOR 'SOCIAL JUSTICE' - Leaked Soros Memo: Refugee Crisis ‘New Normal,’ Gives ‘New Opportunities’ For Global Influence / Sabine Durden's Son Killed By An Illegal...Muslim Refugees in Germany / HALF OF ALL REFUGEES ADMITTED TO USA THIS YEAR: MUSLIM... 30,000+ / Muslim trained to wage jihad allowed into U.S. / MERKEL: Refugees didn't bring terror... Islam belongs in Germany... / GERMAN INTELLIGENCE EXPERT WARNS OF SUICIDE SQUADS HIDING AMONG ASYLUM SEEKERS / Refugees Refuse Work: 'We Are Merkel's Guests!' Germany moves to ban far-right party... / LONDON’S MUSLIM MAYOR INTRODUCES THE THOUGHT POLICE And demonstrates how the Left serves the Islamic supremacist agenda. / - *KINGDOM OF SOROS: INFLUENCE WORLD WITH REFUGEE CRISISCASH FOR 'SOCIAL JUSTICE' - * Leaked Soros Memo: Refugee Crisis ‘New Normal,’ Gives ‘New Opportuniti...1 year ago
Proverbs 22:3 NLT
A prudent person foresees danger and takes precautions. The simpleton goes blindly on and suffers the consequences.
-- (((Charles Finney, said the following: “If
there is a decay of conscience, the pulpit is responsible for it))) --
THOSE WHO WILL DO NOTHING NOW, WHEN IT COSTS THEM LITTLE - WILL DO EVEN LESS LATER, WHEN IT COST THEM EVEN MORE
Preparing for what is coming to America - Prepare to Defend America
LIVE EARTHQUAKE MAP
My Blog List
Is Wal-Mart in Harrison, Arkansas Closing down (Because the Pipes are bad) - [image: Red Flag Warnings To America - A Wake Up Call] A person who I know very well came up to me today. He wanted to tell me about a conversation he ha...1 year ago
‘PATHETIC LIAR’ ANDERSON COOPER ATTACKS TRUMP THEN IMMEDIATELY DOES WHAT YOU EXPECT - Jim Hoft for the Gateway Pundit reports, On Wednesday morning President Donald Trump tweeted out on Judge Roy Moore’s stunning election loss. Read More/Sou...2 hours ago
End Time Talk Radio - (Radio Shows)
X22 Report is a daily show that will cover issues surrounding the economic collapse
Saturday, July 16, 2011
UNUSUAL EVENT DECLARED BASED ON REACTOR COOLANT LEAK GREATER THAN 10 GPM at New Jersey nuke plant after reactor coolant leak — “Leakage outside containment”
read at bottom of Page
UNUSUAL EVENT DECLARED BASED ON REACTOR COOLANT LEAK GREATER THAN 10 GPM
"At 2053 on July 14, 2011 Salem unit 2 declared an Unusual Event due to reactor coolant system leakage greater than 10 gallons per minute. While performing a monthly Emergency Core Cooling System vent of the high head safety injection piping a motor operated valve was opened and a leak developed on the high head piping greater than 10 gallons per minute. The leak rate was approximately 11-15 gallon per minute. The leak was terminated when the motor operated valve was closed. The time of the leak was about 6 minutes."
At this time the leak is believed to be from a crack on the Boron Injection Tank (BIT) relief valve line which is connected to the high head piping. A total of approximately 90 gallon of reactor coolant leaked into the BIT room. The licensee has declared the high head safety injection inoperable and is proceeding to shutdown under Tech Spec 3.0.3.
The license has notified appropriate State and local authorities. The licensee will notify the NRC Resident Inspector.
* * * UPDATE FROM KARL HANPHO TO VINCE KLCO ON 7/15/11 AT 0025 EDT* * *
"Salem Unit 2 declared an Unusual Event due to Reactor Coolant System (RCS) leakage being greater than 10 gpm and pressurizer level decreasing. Leakage was estimated to be approximately 15 gpm. The leakage was determined to be from a weld on the high head charging injection relief valve connection. This leaking weld impacts both trains of high head charging/safety injection. Both trains of high head charging/safety injection were declared inoperable at 2038 [EDT] on July 14, 2011, entering TS 3.0.3. Salem Unit 2 began the Technical Specification shutdown in accordance with TS 3.0.3 at 2136 [EDT]. The technical specification shutdown is being reported in accordance with 10CFR50.72(b)(2)(i) and RAL 11.1.1.a.
"In addition since the leakage from the weld on the high head charging/safety injection piping exceeded the analyzed limit for ESF leakage outside containment, this event is also being reported in accordance with 10CFR50.72(b)(3)(v) and RAL 11.2.2.b as a condition that prevents the ability to mitigate the consequences of an accident.
"Salem unit 2 is currently at 27% and reducing power."
The licensee notified the states of New Jersey and Delaware, Lower Alloways Township and the NRC Resident Inspector.
Notified the R1DO (Dwyer), NRR-EO (Giiter) and IRD (Morris).
* * * UPDATE FROM KARL HANPHO TO CHARLES TEAL ON 7/15/11 AT 0345 EDT* * *
Salem Unit 2 has exited the Unusual Event as of 0339 EDT. The criteria for exit was the leakage rate was below the 10 gpm rate. The plant is in Mode 3 and is preparing to cooldown.